ASTM F1734 2003 Edition, August 10, 2003
Standard Practice for Qualification of a Combination of Squeeze Tool, Pipe, and Squeeze-Off Procedures to Avoid Long-Term Damage in Polyethylene (PE) Gas Pipe
Includes all amendments and changes through Reapproval Notice , 2009
Published By:ASTM International (ASTM)
This practice covers qualifying a combination of a squeeze tool, a polyethylene gas pipe, and a squeeze-off procedure to avoid long-term damage in polyethylene gas pipe. Qualifying is conducted by examining the inside and outside surfaces of pipe specimens at and near the squeeze to determine the existence of features indicative of long-term damage. If indicative features are absent, sustained pressure testing in accordance with Specification D 2513 is conducted to confirm the viability of the squeeze-off process. For assistance with specimen examination, an Adjunct, ADJF17342, is available from ASTM.
This practice is appropriate for any combination of squeeze tool, PE gas pipe and squeeze-off procedure, and is particularly appropriate for pre-1975 Polyethylene (PE) pipe, and for pipe sizes of 8 in. or above, because of a greater possibility of long-term damage.
This practice is for use by squeeze-tool manufacturers, pipe manufacturers and gas utilities to qualify squeeze tools made in accordance with Specification F 1563; and squeeze-off procedures in accordance with Guide F 1041 with pipe manufactured in accordance with Specification D 2513.
Governing codes and project specifications should be consulted. Nothing in this practice should be construed as recommending practices or systems at variance with governing codes and project specifications.
Where applicable in this guide, "pipe" shall mean "pipe and tubing."
Units—The values stated in inch-pound units are to be regarded as standard. The values given in parentheses are mathematical conversions to SI units that are provided for information only and are not considered standard.
This standard does not purport to address all of the safety concerns, if any, associated with its use. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
2 Available from ASTM International Headquarters. Order Adjunct No. ADJF1734. Original adjunct produced in 1995.